Brivis ducted heating Moorabbin,
repairs to these models of Brivis heater series
BX CC HX SP Multiplex He Me 2P Wombat N
Wombat NXA Buffalo Compact Classic StarPro
Heater system with add-on cooling BRIVIS ICE,
Brivis ducted heating repair,
Brivis heater repairs,
Tel: (03) 9700 7059
. Approved parts with full warranty,
. Quick service. Best price everyday ,
. Genuine business. Over 20 years experienced
Repair Brivis ducted heating problems, Control module, Main boards, pcb, Ignitor pcb Motor, Zone system, Wall control, Flame sensor Room blower, Motor, Switch, combustion Fan Electrical, Electronic, Wiring, Relay, Timer Circuit boards, Display, Solenoid, Gas valve pcb, Brivis ICE refrigerated cooling add on system, Error code Spanner on controller, and MORE, .
. from $180 Main module preventative service, circuit rejuvenate, trouble shooting.
. from $80 Module, electric pcb: Workshop testing, fault finding.
Onsite testing and repair of the following ducted heating faults:
FAN Uncontrollable, or continuously, IGNITION problem, weak sparks, Hot surface igniter, ERROR: Fault code errors, LED flashing, random fault, MOTOR bearing and Mechanical noise, NOISE: Intermittent humming noise, Buzzing noise, THERMOSTAT responsive problem, ELECTRICAL CB, RCD trip, GAS VALVE beating noise, Shuts gas valve off intermittently, Will not ignite, SELF RESET, Control board self resetting, Heating CYCLING, heater attempts to start then shut down immediately, NOT RESTART, Will not restart after the first heating cycle, Heater’s reached set room temperature then stop working and will not restart, Service SPANNER and service ERROR CODE on display, Requires MANUAL RESET on controller so often, INTERMITTENT locking noise from the gas valve, Room FAN BLOWER MOTOR not working, PILOT not working.
Repairs to all Brivis heater module, pcb,
Obsolete electronic parts. HVAC-R circuits,
Brivis ducted heating add on Brivis ICE cooling,
Brivis Classic Series Brivis 2P Wombat 15, 20, 20XA, 26, 26XA, Brivis Buffalo 15, 20, 20XA, 26XA, Brivis Downflow 20, 20XA, Brivis Upflow 20, 20XA, 26, 26XA,
Brivis Compact Classic Series CC315IN, CC320IN, CC320IN-XA, CC325IN, CC325IN-XA, CC330IN, CC330IN-XA,
Brivis StarPRo SP4 Series SP415, SP421, SP430, SP435,
Brivis StarPro MX Series MX21E, MX21E-XA, MX21I, MX21I-XA, MX30E, MX30E-XA, MC30I, MC30I-XA, MX35I,
Brivis Buffalo 5 Star Series BX520 BX526,
Brivis StarPro Sp5 Series SP515IN, SP521EN, SP521EN-XA, SP521IN, SP521IN-XA, SP530EN, SP520EN-XA, SP530IN, SP530IN-XA, SP535IN,
Brivis StarPro HX Series HX15I, HX23E, HX23E-XA, HX23I, HX23I-XA, HX30E, HX30E-XA, HX30I, HX-30I-XA, HX35I,
Brivis StarPro SP6 Series Sp615IN, SP623EN, SP623EN-XA, SP623IN, SP623IN-XA, SP630EN, SP630EN-XA, SP630IN, SP630IN-XA, SP635IN,
. Best prices everyday.
. Genuine and insured business.
. Approved parts with warranty.
. Prompt. Honest. Experienced.
———————————Tel: (03) 9700 7059
If your heater is not working as it should: 90% changes are the Electronic parts faulty. You then have 4 choices: (1). Replace whole new system regardless the manufacturer's diagnostic error code, because you had 3 quotes from an electrician, plumber and a handyman. (2). Utilising my specialty heating electronic repair skills making the heater back to work as soon as you possibly want; ''If its beyond repair'': You only pay me for the fault finding. (3). Call manufacturer: Pay call out fee. Until appointment, take a day-off-work, senselessly wait for the tech arrives. So far, no repair guaranteed. (4). Call local heating repair contractors: Same as the (3), some charge excessively just to come, Some are even lacking manufacturer training and equipment. . All modern BRIVIS ducted heaters have CPU and Electronic circuits, these are way too difficult for an average trade person who then often suggesting a new system replacement. Before that, call us for a final inspection: The problem sometimes just simply a fault component on electrical system, or can be rectified as cheap as a fraction the costs compared to replacing a whole new heating system.
Fix2Qik Refrigeration, Air conditioning © Allright Reserved.
Brivis heater error code reset service and repairs,
Brivis EMS, MPS, StarPro, BMax, SP, BX models,
Error30, FAN_LIMP, Fault code FAN SENSOR,
Error31, RoLL_TERR, WRONG FLAME sequence,
Error32, DATA_Err, CONTROL module malfunction,
Error35, No_SA-THM, Thermistor circuit faulty,
Error36, BAdSA-THM, Thermistor circuit faulty,
Error37, TACHO-Err, Irregular MOTOR speed,
Error40, OHEAT_xx, Fault code OVERHEAT,
Error41, OHEAT_xx, Fault code OVERHEAT,
Error42, OHEAT_xx, Fault code OVERHEAT,
Error43, OHCoolDwn, Motor Cooling ON, from 40, 41, 42,
Error44, RoLLOut, FlAME detected on Afro rod,
Error45, LOW24VOLT, Insufficient POWER SUPPLY,
Error46, IGN_RETRY, Too MANY Ignition attempts,
Error47, IGN_RETRY, Fail to light in time,
Error50, IGN_LKOUT, Ignition LOCKOUT no Burner,
Error51, FLMS_LOSS, Pilot FLAME unsuccessful,
Error52, FLM_NOGAS, FLAME On while VAVLE’s Off,
Error53, OH_LKOUT, 2 consecutive OVER-TEMPERATURE,
Error54, RoL_LKOUT, LOCKED after 3 of Error 44,
Error55, IGNINVALID, Lost Flame in 10 seconds,
Error56, PowER_UPD, Power Interrupt, Unreached Vacuum,
Error60, MOTOR_O-C, Fan MOTOR problem,
Error61, 503_FAIL1, NG1/lo main control failure,
Error62, HSI_LOCK, Electronic IGNITOR problem,
Error63, 503_FAIL5, NG1/lo Main control trouble,
Error64, 503_FAIL, NG1/lo EEPROM loading failure,
Error65, MTR_LKOUT, Main Motor room fan stalling,
Error67, 503_WD, NG/lo PCB faulty,
Error68, 503nCCFG_Err, NG/lo PCB faulty,
Error69, FUSE_BLOW, 24VAC fuse open circuit,
Error70, FSAFE_LOC, Flame LOSS Back up sensor,
Error71, FSaFE_LOC, Flame LOSS Back up sensor,
Brivis Compact Classic CC3-15,20,25,30,
Error code service, reset and repairs,
One Flash, Over heat Problem,
Two Flash, Unachieved Vacuum,
Three Flash, No start up flame,
Four Flash, Pressure problem lock out,
Five Flash, Ignition problem lock out,
Six Flash, Gas Valve fault, Main Control fault,
Brivis Wombat, Buffalo, DownFlow, Upflow, HCCA621 models,
Error code service, reset and repairs,
One flash, Overheat condition, reset by user,
Two Flashes, Many Overheat detected, LOCK OUT,
Three Flashes, Flame rolls out of heat exchanger,
Four Flashes, Many Roll out, LOCK OUT,
Five Flashes, SAFE Start Lock Out,
Six Flashes, Ignition invalid, LOCK OUT,
Seven Flashes, Gas Valve fail, Lock Out,
Eight Flashes, Frequency, Lock Out,
Brivis Classic Buffalo 52, Buffalo 85,
Buffalo 120, Wombat 52, Wombat 92, Wombat 120,
Upflow 92, Upflow 120, Downflow 92,
TEK311, TEK321, TEK322, BCG-1, TEK331,
Error Codes service, reset and repairs,
LED Code Identification
AOG Green, Error Recovery Occurred,
STAT Green, Thermostat and Fan indicator,
FAN Green, Fan motor is ON,
ECON, not for user,
ROLL, red and Solid, indicates Flame rolled out,
ROLL, red and Flashing, many roll out detected, LOCK OUT,
OH/S, red and Solid, indicates Overheated condition,
OH/S, red and Flashing, Fan On due to Overheated condition,
OH/F, red and Solid, Fans over temperature,
OH/F, red and Flashing, Lock out due to Fans problem,
All LED illuminated, all LED flickering, flashing unrecognisable, Indicates Control PCB problem.Tel: (03) 0420 982 770
Please contact me for a solution if there is any other abnormal operating condition of your heater, and rest assure that I am taking care of the problem promptly,
Electronics and electro-mechanical parts are the major cause of over 90% heater’s faults, and you would likely experiencing symptom like these: (not all listed).
Gas valve’s life cycle: A gas valve of a good known brand heater is working fine in upto between 120000 to 150000 cycles. It is normal to see many 30 years old heaters that have been using in average 8 to 10 hours per day, or less of heating are still working fine.
loosely calculation showing more than 1/2 of my heater’s running cost annually is spending on electrical. Because even the gas burner is off, many electric parts are still being energised for the purpose of sensing, safely monitoring and standing-by, waiting to kick the rest of the heater into action once it received instructions from controller.
Electric costs remain virtually the same in summer (yes! summer) if the heater being used in “Fan-only” mode to circulate the nearby cooled air from one air conditioning room; Often from the main living room; to the other areas of the house.
So, Even though categorised as Gas appliance, the 90% of parts that making up the heater are running on electric, proportionally the 90% of all faults are electric related problems.
Local technician repairs Ducted Heating system
Term & Condition:
* Repair guarantee: Part and labour 12 months, or per specified. * All repairs include manufacturer instruction (if any), ESV compliant certificate * Guaranty and refund excluding: OEM recall, factory defect. Freights, travels. Part(s) reclaiming impossible with 30 days including postage delay. Uncollected items will be disposed after 30 days since informed. Free repair quotation and estimate but fault finding, travelling and parking from or to job sites incurring extras: Please call for details.
Disclaimer: Brand names and trademarks are belong to their respective owners, and being used here for descriptive purposes only.. Fix2Qik is not operating the same as a plumbing contractor business. Does not provide quotation on new or old ducting job. Not installing new heating system or change over. No schedule servicing. No carbon monoxide testing. No gas fitting. No plumbing quotes. All plumbing works will be forwarded to the associate tradesmen once required.